# Analog Input Module
The Analog Input Module is used to receive data from analog devices with a 0…20 mA signal, RS-485 interface and Wireless connection is used for communication with the module. For example: a valve, a sensor and others. The Analog Input Module sends the collected data to the Enapter Gateway and Cloud via secure wireless connection.
# Technical Data
|Voltage||9…24 V DC|
|Connected sensors number||4 x Analog sensors|
|Wireless Communication||Wi-Fi 2.4 GHz|
Bluetooth 4.0 LE
|Integrated connection type||Isolated RS-485 interface|
|Antenna connection type||SMA-F (module) – SMA-M (antenna)|
|Local signaling||1 LED (green): steady – correct operation, blinking – establishing connection with server|
1 LED (red): module error
|Current consumption||50 mA 12 V DC, max. 300 mA|
|Mounting||35 mm Din rail acc. to IEC 60715|
|Height||90.2 mm (3.55 inch)|
|Depth||57.5 mm (2.26 inch)|
|Width||36.3 mm (1.43 inch)|
|Net weight||0.090 kg|
# Environmental Conditions
|Ambient air temperature for operation||-40…+60 ℃|
|Ambient air temperature for storage||-40…+60 ℃|
|Relative humidity for operation||20…90 %, without condensation|
|Relative humidity for storage||20…90 %, without condensation|
|Operating altitude||0…2000 m|
|Storage altitude||0…3500 m|
|IP degree of protection||IP20|
# Connected Device
|Connection||Screw terminal block|
|Signal resolution||16 bit|
|Galvanic isolation||Group, from controller circuits|
The dimensions are in mm and in brackets in inch.
The ENP-AI4-20MA Module must be horizontally mounted on 35 mm DIN rail according to IEC 60715.
# Connection Example
1 Amp Circuit Breaker recommended to use on power line for the ENP-AI4-20mA Module.
Wi-Fi protocols – 802.11 b/g/n/e/i (802.11n up to 150 Mbit/s).
Bluetooth protocols – Bluetooth v4.2 BR/EDR and BLE specification.
Alternating current voltage of 110 - 220 V is potentially lethal!
All works on assembly and installation should be performed only with a disconnected power supply!
The installation and assembly of electrical equipment must be carried out by electrically qualified persons.
The appearance of the product may differ from the images presented on the website or in this manual. The discrepancy between the appearance and packaging of the goods with a picture and description on the website or this manual is not an indication of poor quality goods. The manufacturer reserves the right to make changes to the design and packaging of the product without prior notice.
# Lua API
Lua API lets to interact with 3rd party devices via our UCMs (opens new window). It includes functions that implement various kinds of interaction. For more information please visit Enapter Developer Toolkit (opens new window) and ENP-AI4 Reference (opens new window).
ENP-AI4-20mA Module Datasheet (EN)
ENP-AI4-20mA Module Quick Start Guide (EN)
ENP-AI4-20mA Module CAD Drawings (2D)
ENP-AI4-20mA Module CAD Drawings (3D DWG)