# Digital Input Module
Digital Input Module is used to monitor the status of discrete signals such as contactors, relays and others. ENP-DI7 Module can work in wet or dry contact modes (set by the jumper inside the module). The Digital Input Module sends the collected data to the Enapter Gateway and Cloud via secure wireless connection.
# Technical Data
|Voltage||9…24 V DC|
|Wireless Communication||Wi-Fi 2.4 GHz|
Bluetooth 4.0 LE
|Integrated connection type (optional)||Isolated RS-485 interface|
|Antenna connection type||SMA-F (module) – SMA-M (antenna)|
|Local signaling||1 LED (green): steady – correct operation, blinking – establishing connection with server|
1 LED (red): module error
|Current consumption||50 mA 12 V DC, max. 300 mA|
|Mounting||35 mm Din rail acc. to IEC 60715|
|Height||90.2 mm (3.55 inch)|
|Depth||57.5 mm (2.26 inch)|
|Width||36.3 mm (1.43 inch)|
|Net weight||0.090 kg|
# Environmental Conditions
|Ambient air temperature for operation||-40…+60 ℃|
|Ambient air temperature for storage||-40…+60 ℃|
|Relative humidity for operation||20…90 %, without condensation|
|Relative humidity for storage||20…90 %, without condensation|
|Operating altitude||0…700 m|
|Storage altitude||0…3500 m|
|IP degree of protection||IP20|
# Connected Digital Device
|Number of connected devices||Up to 7|
|Connection||Screw terminal block|
|Galvanic isolation||Group, from controller circuits|
|Wet contact voltage||12 V|
# Connected RS-485 Device (optional)
Power meter and others
|Voltage supply||9 - 24 V DC when module and RS-485 device powered from shared power supply|
|Connection||2-pin screw terminal block|
The dimensions are in mm and in brackets in inch.
The ENP-DI7 Module must be horizontally mounted on 35 mm DIN rail according to IEC 60715.
# Connection Example
# Optional RS-485 Device Connection Examples
1 Amp Circuit Breaker recommended to use on power line for the ENP-DI7 Module.
Wi-Fi protocols – 802.11 b/g/n/e/i (802.11n up to 150 Mbit/s).
Bluetooth protocols – Bluetooth v4.2 BR/EDR and BLE specification.
Alternating current voltage of 110 - 220 V is potentially lethal!
All works on assembly and installation should be performed only with a disconnected power supply!
The installation and assembly of electrical equipment must be carried out by electrically qualified persons.
The appearance of the product may differ from the images presented on the website or in this manual. The discrepancy between the appearance and packaging of the goods with a picture and description on the website or this manual is not an indication of poor quality goods. The manufacturer reserves the right to make changes to the design and packaging of the product without prior notice.