# Relay Module
The Relay Module is used to control of a low-power load without high inrush currents. For example: a normal closed valve, a normal open valve, signal lamps or intermediate contactors. The Relay Module sends the collected data to the Enapter Gateway and Cloud via secure wireless connection.
# Technical Data
|Voltage||9…24 V DC|
|Wireless Communication||Wi-Fi 2.4 GHz|
Bluetooth 4.0 LE
|Antenna connection type||SMA-F (module) – SMA-M (antenna)|
|Local signaling||1 LED (green): steady – correct operation, blinking – establishing connection with server|
1 LED (red): module error
|Current consumption||50 mA 12 V DC, max. 300 mA|
|Mounting||35 mm Din rail acc. to IEC 60715|
|Height||90.2 mm (3.55 inch)|
|Depth||57.5 mm (2.26 inch)|
|Width||36.3 mm (1.43 inch)|
|Net weight||0.090 kg|
# Environmental Conditions
|Ambient air temperature for operation||-40…+60 ℃|
|Ambient air temperature for storage||-40…+60 ℃|
|Relative humidity for operation||20…90 %, without condensation|
|Relative humidity for storage||20…90 %, without condensation|
|Operating altitude||0…700 m|
|Storage altitude||0…3500 m|
|IP degree of protection||IP20|
# Connected Device
|Type||Normal closed valve|
Normal open valve
|Connection||Screw terminal block|
|Contact Configuration||Normally open|
|Output Configuration||Two groups of 3 outputs,|
a common wire in each group
|Maximum switching voltage||AC 250 V|
|Maximum switching voltage||DC 30 V|
|Maximum switching current per channel||7 A|
The dimensions are in mm and in brackets in inch.
The ENP-RL6 Module must be horizontally mounted on 35 mm DIN rail according to IEC 60715.
# Connection Example
1 Amp Circuit Breaker recommended to use on power line for the ENP-RL6 Module.
Wi-Fi protocols – 802.11 b/g/n/e/i (802.11n up to 150 Mbit/s).
Bluetooth protocols – Bluetooth v4.2 BR/EDR and BLE specification.
Alternating current voltage of 110 - 220 V is potentially lethal!
All works on assembly and installation should be performed only with a disconnected power supply!
The installation and assembly of electrical equipment must be carried out by electrically qualified persons.
The appearance of the product may differ from the images presented on the website or in this manual. The discrepancy between the appearance and packaging of the goods with a picture and description on the website or this manual is not an indication of poor quality goods. The manufacturer reserves the right to make changes to the design and packaging of the product without prior notice.
# Lua API
Lua API lets to interact with 3rd party devices via our UCMs (opens new window). It includes functions that implement various kinds of interaction. For more information please visit Enapter Developer Toolkit (opens new window) and ENP-RL6 Reference (opens new window).