# CAN Bus Module
The CAN Bus Module is used to read data from devices such as vehicles, inverters, ventilation systems, valves, irradiance sensors, power meters and others. The CAN Bus Module sends the collected data to the Enapter Gateway and Cloud via secure wireless connection.
# Technical Data
|Voltage||9…60 V DC|
|Wireless Communication||Wi-Fi 2.4 GHz|
Bluetooth 4.0 LE
|Integrated connection type||CAN bus|
|Antenna connection type||SMA-F (module) – SMA-M (antenna)|
|Local signaling||1 LED (green): steady – correct operation, blinking – establishing connection with server|
1 LED (red): module error
|Current consumption||50 mA 12 V DC, max. 300 mA|
|Mounting||35 mm Din rail acc. to IEC 60715|
|Height||90.2 mm (3.55 inch)|
|Depth||57.5 mm (2.26 inch)|
|Width||18.1 mm (0.71 inch)|
|Net weight||0.050 kg|
# Environmental Conditions
|Ambient air temperature for operation||-40…+60 ℃|
|Ambient air temperature for storage||-40…+60 ℃|
|Relative humidity for operation||20…90 %, without condensation|
|Relative humidity for storage||20…90 %, without condensation|
|Operating altitude||0…2000 m|
|Storage altitude||0…3500 m|
|IP degree of protection||IP20|
# Connected device
|Voltage supply||9…60 V DC when module and device|
powered from shared power supply
|Connection||2-pin screw terminal block|
The dimensions are in mm and in brackets in inch.
The ENP-CAN Module must be horizontally mounted on 35 mm DIN rail according to IEC 60715.
# Connection Examples
1 Amp Circuit Breaker recommended to use on power line for the ENP-CAN Module.
Wi-Fi protocols – 802.11 b/g/n/e/i (802.11n up to 150 Mbit/s).
Bluetooth protocols – Bluetooth v4.2 BR/EDR and BLE specification.
Alternating current voltage of 110 - 220 V is potentially lethal!
All works on assembly and installation should be performed only with a disconnected power supply!
The installation and assembly of electrical equipment must be carried out by electrically qualified persons.
The appearance of the product may differ from the images presented on the website or in this manual. The discrepancy between the appearance and packaging of the goods with a picture and description on the website or this manual is not an indication of poor quality goods. The manufacturer reserves the right to make changes to the design and packaging of the product without prior notice.
# Lua API
Lua API lets to interact with 3rd party devices via our UCMs (opens new window). It includes functions that implement various kinds of interaction. For more information please visit Enapter Developer Toolkit (opens new window) and ENP-CAN Reference (opens new window).
# The Module Is Not Receiving Telemetry
Check the jumpers inside the ENP-CAN module (install if needed):
- Dismount the antenna from the ENP-CAN module.
- Remove the front cover.
- Remove the back side of the module.
- Carefully push the module control board down.
- Install jumper J5, jumper J3 H.speed or both according to the picture below.