# RS-232-MPP Module
The RS-232-MPP Module monitor and manage MPP Solar Inverters with RS-232 port and Watchpower Serial Protocol. It sends the collected data to the Enapter Gateway and Cloud via secure wireless connection. The RS-232-MPP Module is based on Enapter RS-232 Module.
# Technical Data
|Voltage||9…60 V DC|
|Standardized Wire Gauge||AWG 17 (1 sqm2)|
|Wireless Communication||Wi-Fi 2.4 GHz|
Bluetooth 4.0 LE
|Integrated connection type||RJ-10/4P4C|
|Antenna connection type||SMA-F (module) – SMA-M (antenna)|
|Local signaling||1 LED (green): steady – correct operation, blinking – establishing connection with server|
1 LED (red): module error
|Current consumption||50 mA 12 V DC, max. 300 mA|
|Mounting||35 mm Din rail acc. to IEC 60715|
|Height||90.2 mm (3.55 inch)|
|Depth||57.5 mm (2.26 inch)|
|Width||18.1 mm (0.71 inch)|
|Net weight||0.050 kg|
# Environmental Conditions
|Ambient air temperature for operation||-40…+60 ℃|
|Ambient air temperature for storage||-40…+60 ℃|
|Relative humidity for operation||20…90 %, without condensation|
|Relative humidity for storage||20…90 %, without condensation|
|Operating altitude||0…2000 m|
|Storage altitude||0…3500 m|
|IP degree of protection||IP20|
# Connected device
|Type||Watchpower Serial Protocol Inverters|
(MPP Solar, Axpert, SILA, etc)
|Connection to Module||RJ-10/4P4C|
|Connection to MPP Solar Inverter||RJ-45/8P8C|
|Connection Cable Length||1.0 m|
The dimensions are in mm and in brackets in inch.
The ENP-RS232-MPP Module must be horizontally mounted on 35 mm DIN rail according to IEC 60715.
# Connection Examples
1 Amp Circuit Breaker recommended to use on power line for the ENP-RS232-MPP Module.
# Connection Cable Pinout
|RJ-10 Pin||RJ-10 Signal||RJ-10 Wire Color||RJ-45 Wire Color||RJ-45 Signal||RJ-45 Pin|
Wi-Fi protocols – 802.11 b/g/n/e/i (802.11n up to 150 Mbit/s).
Bluetooth protocols – Bluetooth v4.2 BR/EDR and BLE specification.
Alternating current voltage of 110 - 220 V is potentially lethal!
All works on assembly and installation should be performed only with a disconnected power supply!
The installation and assembly of electrical equipment must be carried out by electrically qualified persons.
The appearance of the product may differ from the images presented on the website or in this manual. The discrepancy between the appearance and packaging of the goods with a picture and description on the website or this manual is not an indication of poor quality goods. The manufacturer reserves the right to make changes to the design and packaging of the product without prior notice.